Industry-Leading Aircraft Services Company
Stormwater Filtration Challenge
Whether protecting life and property by fighting fires, performing low-impact logging or providing disaster relief and reconstruction efforts around the world, our client has a long history of doing the right thing. In fact, their core values are engineered to ensure employee health and safety and environmental stewardship:
• Comply with all applicable health, safety and environmental regulations and laws, and global HSE standards
• Ensure a non-punitive safety environment to encourage reporting of incidents, hazards and safety-related concerns.
• Act to minimize the environmental impact of its activities
• Educate and motivate employees and contractors to conduct their activities in a safe and environmentally responsible manner.
Consistent adherence to these values is just one of the reasons that our client has received numerous awards for employer excellence from federal aviation authorities.
ELEVATED ZINC LEVELS & COMPETITIVE ANALYSIS DRIVES PROCUREMENT OF CLEANWAY DOWNSPOUT FILTRATION DEVICES
The facility in question was one of our client’s fleet maintenance and repair facilities. While the facility, at 3.898 acres and 51,000 square feet might be considered small by some standards, the combination of the fleet’s refueling, chase and service vehicles, and associated fuels and cargo, added complexity to identifying the pollutant source. When scheduled testing at two catch basin compliance points adjacent to the structure showed elevated zinc levels, our client’s legal department contacted CleanWay to order six (6) downspout filtration devices. Because our client’s Environmental Health and Safety department was undergoing restructuring, legal stepped into the research and procurement role.
After competitive analysis, our client selected the downspout filtration system from CleanWay for its superior, high capacity design, “plug and play” installation and ease of maintenance. Each downspout device was fitted with CleanWay’s patented MetalZorb filtration media packs.
“CleanWay recognized the need for rooftop stormwater and downspout filtration over 20 years ago. As a result, we’ve continuously refined our downspout filtration system (also referred to as roof drain filters, gutter drain filters or rainwater filters) to meet the evolving needs of our customers. Unlike inline options, which require cutting and fitting of the existing downspout, our units are free standing, easily accessible for maintenance and cleaning and incorporate a patented water sampling port for verifiable filtration performance. Two levels of outlet openings allow the unit to be run in either a dry (where vector control is a concern) or wet configuration (to increase removal rates with additional contact time).”
Matthew Moulton, General Manager, CleanWay Environmental Partners
After installation of the downspout filters, zinc levels immediately decreased, in fact, zinc levels at Port II, Basin 3 went from .457 mg/L to below benchmark in late November of 2016. However, levels remained stubbornly above the 1200-Z permit benchmark at Port I, Basin 1. It’s significant to note that testing was being done downstream of the downspout filters at the two catch basins adjacent to the fleet maintenance structure. These two catch basins were the testing compliance points identified in our client’s SWPPP, but with the structural change of added downspout filtration, CleanWay suggested testing at all filtration points. It appeared our client, with CleanWay’s help, was moving toward sustainable compliance when nature intervened.
“PERFECT STORM” OF EXTREME WEATHER AND DEFERRED MAINTENANCE SPUR ENHANCED BMPS AND “TUNED” FILTRATION MEDIA
In December 2016 and much of January 2017, a historic cycle of freezing rain and snow followed by brief thaws hit the area. When the thaw came about in early February 2017, our client’s stormwater facility experienced unprecedented runoff, and dramatically increased zinc levels as tested at the catch basins; 1.734 mg/L at Basin 3 and 1.397 mg/L at Basin 1.
Our client immediately contacted an environmental consulting firm to identify the source of the excessive zinc runoff. On the recommendation of the environmental consulting firm, our client commissioned the coating (by an outside company) of all galvanized roof surfaces (in May 2017); the excavation of collection points for improved sampling; and jetting and scoping of all stormwater facility lines (performed by River City Environmental). CleanWay also “tuned” it’s downspout filtration media with specially blended filtration packs at each downspout filtration device incorporating MetalZorb media blended with biochar; All of this work was completed in late May of 2017.
TEST RESULTS AND FINANCIALS YIELD IMPRESSIVE COST/BENEFIT NUMBERS
Test results after installation of CleanWay downspout filtration devices and associated facility maintenance was an impressive 0.059mg/L for Port I, Basin 1 and 0.007 for Port II, Basin 3.
Cost Per Square Foot of The Comprehensive Program:
• Initial CleanWay Downspout Install: $0.24 Sq/ft
• CleanWay Filter & Media Upgrade: $0.10 Sq/ft
• Power Wash & Roof Painting: $0.49 Sq/ft
• Excavate Sample Locations: $0.14 Sq/ft
• Stormwater Pipe Flush: $0.02 Sq/ft
Total annual O&M cost (CleanWay filters and media) per square foot of roof is an equally impressive $0.10
With over 25 years of experience, CleanWay Environmental Partners is dedicated to providing clients with affordable stormwater runoff solutions. Located in Portland, OR, our skilled staff is committed to serving customers nationwide with first-rate catch basin filters, downspout filtration units, premium leachate treatments, and heavy metals extraction products. Call (800) 723-1373 to request a quote and to learn more about how we can help you comply with environmental regulations.
Request Your Free Quote Today
How can we help you?